Diesel Generators for Sale in Brisbane, Melbourne, and Perth
The Importance of Rating diesel generators Engines Correctly
When looking to purchase a generator the first thing to consider is the intended use. It may seem obvious what power rating is required for an application but there are a number of factors to consider before purchasing a generator. The guidelines set forth in this article will better explain the proper application of generator drive engines in AC Generator Set installations.
Standby power rated diesel generators are the most commonly rated generator sets. Their primary application is to supply emergency power for a limited duration during a power outage. With standby rated generators there is no overload capability built into the units. It is important to note that standby rated generators, under no circumstances, should run in conjunction with a public utility source.
Standby power rating should be applied to the unit where public utility power is available. The typical rating for a standby engine should be sized for a maximum of 80% average load factor and roughly 200 hours per year. This includes less than 25 hours per year of running time at the standby rating. Standby power ratings should never be applied except in true emergency outage situations. Predetermined outages with the utility company, under UL guidelines, are not considered emergency outages. Manual load shifts for testing purposes can be performed with most automatic transfer switches.
Prime power rated generators should be used in applications where the user does not purchase power from a public utility. Prime power applications fall under two distinct categories:
The prime power rating is the maximum power accessible at the variable load for an unlimited number of hours per year in a variable load setting. It is not advisable that the variable load exceed 70% average of the prime power rating during any operational period of 250 hours. If the engine is running at 100% prime power, yearly hours should not exceed 500. Overload situations should be avoided however a 10% overload capability is available for a 1 hour period within a 12-hour cycle of operation.
Prime power is accessible for a limited number of hours in non-variable load situations. Limited prime power is intended for circumstances where power outages are expected, such as a planned utility power reduction. Engines in generator sets may operate up to 750 hours per year at power levels less than the maximum prime power rating. In these situations, it is important to never exceed the prime power rating. The end user should be aware that constant high load use will reduce the life of an engine. It is recommended that any application requiring over 750 hours per year that the engine be continuous power rated.
Continuous power rating is used in applications where supplying power is at a constant 100% load for an unlimited number of hours each year. Continuous power rated units are most widely used in applications where the power grid is unreachable. Such applications include mining, agriculture or military operations.
Diesel generators Sydney
Diesel generators Australia
Generator for sale Sydney
Shop for Gensets Water Cooled Gensets Best Power Options for Successful Off-Grid Living Baldwin Filters for sale Generators Australia for sale Able Sales Perth Gensets oil-fuel or Petrol for sale find your closest generator store Sydney Adelaide